The automatic urinal flush KEG-1022AD is an auto urinal flush valve that integrates electronic sensors, valves, and control processes together. It uses active infrared automatic sensor technology. When you stand in front of the auto flush valve, 2s pre-flush after detection; 6s Flush automatically after leaving. The sensor is integrated inside the valve. A means AC power which can use a power adapter plug to connect alternating current. D means DC with 4 AA 6V alkaline batteries
Auto Urinal Flusher Valve KEG-1022AD Specification
|External Power Supply||Applicable water pressure||Applicable Water Temperature||Ambient Temperature||Feedwater caliber||Flushing water volume|
|4XAA batteries||AC:110v-240V,50Hz-60Hz||DC&AC combined||0.05-0.7Mpa||0.1-60℃||0.1-45℃||G1/2”||1.5-4L(10s based on water pressure of 0.3-0.6Mpa)|
Motion sensor for Automatic Urinal Flusher
As the most important part, the work of the sensor is to forward the signals to the valve to turn on the urinal flusher after detecting your body. Its job is to inform the valve when to turn on or off the water when your body comes and leaves. The cover of the sensor is made by plastic ABS or PA and there is an electronic circuit board inside the sensor eye which also includes the led light.
Normally the sensor eye is placed on the metal faceplate. Mostly the plate is made by stainless steel, some may using cheaper plastic material.
Normally the material of the sensor cover is plastic ABS or PA, the infrared beams can pass through it. Kege have about 50 types of the different sensor head for the selection. We can also customize the sensor cover according to your products.
How to install automatic urinal flush?
Dig a suitable hole on the wall according to the installation instruction. Inter control box into the wall and connect the inlet pipe and outlet pipe. Open the stop-valve to ensure all the connectors are watertight.
The distance between the housing surface and the ceramic tiles should be longer than 15mm.
Adjust the position of the control box, fixed with pieces of wood or other fillers. Then cover the control box by protecting board to avoid the solenoid valve be damaged when filling the cement around the control box. Finally, laying the tiles.
The protecting board should be taken down when finished.
1. A wire connected to the 220V power source should be laid before placing the control box into the wall.
2. Connect the connectors as shown right, place the power supply box as figure 1 shows.
3. Connect the power supply box to the power source.
4. Fix the auto urinal flush face plate on the control box.
Please shut off the power source during the installation.
Auto Urinal Flusher Valve Troubleshooting
|Problem||Possible Reason||Suggested Solution|
|No water flow||Batteries run out||Replace batteries|
|Dirt on sensor surface||Clean the sensor surface|
|Main water supply is shut off||Turn main water supply on|
|Dirt on water filter net||Clean the water filter net|
|Water pressure is not applicable||Refer to technical specification|
|Have a continuous water flow problem||Batteries run out||Replace batteries|
|Low water pressure||Refer to technical specification|