CERAMIC URINAL SENSOR FLUSH VALVE
The ceramic urinal sensor flush valve or flushometer is concealed inside the ceramic sets, you can see the sensor window panel on top of the ceramic urinal set. The panel comes with durable and rustless stainless steel raw material, it is easy to clean and install. It’s totally touch free, reduces virus spreading during the worldwide pandemic. You can either use DC 4XAA alkaline batteries or connect with AC power.
Both durable brass solenoid valves or cheaper plastic valves are workable.
Brass solenoid valve
Durable brass raw material, high quality, rustless but with a higher rate.
Plastic solenoid valve
Cheaper solenoid valve,life time last almost 10 years.
DC battery box
DC battery box with 4XAA alkaline batteries
AC POWER adapter
AC Power adapter with coonnector or wire to connect with AC power.
Ceramic Auto Urinal Flusher Valve KEG-110AD Specification
|External Power Supply||Applicable water pressure||Applicable Water Temperature||Ambient Temperature||Feedwater caliber||Flushing water volume|
4XAA 6V batteries
|AC:110v-240V,50Hz-60Hz||DC&AC combined||0.05-0.7Mpa||0.1-60℃||0.1-45℃||G1/2”||1.5-4L(10s based on water pressure of 0.3-0.6Mpa)|
How to install automatic urinal flush?
Dig a suitable hole on the wall according to the installation instruction. Inter control box into the wall and connect the inlet pipe and outlet pipe. Open the stop-valve to ensure all the connectors are watertight.
The distance between the housing surface and the ceramic tiles should be longer than 15mm.
Adjust the position of the control box, fixed with pieces of wood or other fillers. Then cover the control box by protecting board to avoid the solenoid valve be damaged when filling the cement around the control box. Finally, laying the tiles.
The protecting board should be taken down when finished.
- 1. A wire connected to the 220V power source should be laid before placing the control box into the wall.
- 2. Connect the connectors as shown right, place the power supply box as figure 1 shows.
- 3. Connect the power supply box to the power source.
- 4. Fix the auto urinal flush face plate on the control box.
Please shut off the power source during the installation.
Touchless Urinal Flusher Valve Troubleshooting
|Problem||Possible Reason||Suggested Solution|
|No water flow||Batteries run out||Replace batteries|
|Dirt on sensor surface||Clean the sensor surface|
|Main water supply is shut off||Turn main water supply on|
|Dirt on water filter net||Clean the water filter net|
|Water pressure is not applicable||Refer to technical specification|
|Have a continuous water flow problem||Batteries run out||Replace batteries|
|Low water pressure||Refer to technical specification|