Wall Mounted Automatic Sensor Urinal Flusher KEG-1066AD
The Automatic Sensor Urinal Flusher KEG-1066AD is wall mounted installed on the wall, with an infrared sensor on top of the steel panel, when people stand in front of the auto flush valve, the sensor detects and active 2s pre-flush, and 6s Flush automatically after leaving.
With a press button under the sensor, even when the sensor is no power, you can still press the button to activate manual flush.
Auto Urinal Flusher Valve KEG-1066AD Specification
|External Power Supply||Applicable water pressure||Applicable Water Temperature||Ambient Temperature||Feedwater caliber||Flushing water volume|
|AC:110v-240V,50Hz-60Hz||DC&AC combined||0.05-0.7Mpa||0.1-60℃||0.1-45℃||G1/2”||1.5-4L(10s based on water pressure of 0.3-0.6Mpa)|
INDUCTIVE URINAL FLUSH SENSOR KEG-K1066
As the most important part, the work of the sensor is to forward the signals to the valve to turn on the urinal flusher after detecting your body. Its job is to inform the valve when to turn on or off the water when your body comes and leaves. The cover of the sensor is made by plastic ABS or PA and there is an electronic circuit board inside the sensor eye which also includes the led light.
The sensor rang and flushing time can be adjusted by a remote controller. It washes automatically every 24 hours to avoid the peculiar smell caused by water drying in the water trap.
Kege have about 50 types of the different sensor head for the selection. We can also customize the sensor cover according to your products.
Dig a suitable hole on the wall according to the installation instruction. Inter control box into the wall and connect the inlet pipe and outlet pipe. Open the stop-valve to ensure all the connectors are watertight.
The distance between the housing surface and the ceramic tiles should be longer than 15mm.
Adjust the position of the control box, fixed with pieces of wood or other fillers. Then cover the control box by protecting board to avoid the solenoid valve be damaged when filling the cement around the control box. Finally, laying the tiles.
The protecting board should be taken down when finished.
1. A wire connected to the 220V power source should be laid before placing the control box into the wall.
2. Connect the connectors as shown right, place the power supply box as figure 1 shows.
3. Connect the power supply box to the power source.
4. Fix the auto urinal flush face plate on the control box.
Please shut off the power source during the installation.
Touchless Urinal Flusher Valve Troubleshooting
|Problem||Possible Reason||Suggested Solution|
|No water flow||Batteries run out||Replace batteries|
|Dirt on sensor surface||Clean the sensor surface|
|Main water supply is shut off||Turn main water supply on|
|Dirt on water filter net||Clean the water filter net|
|Water pressure is not applicable||Refer to technical specification|
|Have a continuous water flow problem||Batteries run out||Replace batteries|
|Low water pressure||Refer to technical specification|